In the production of bottled mineral water, the water passes through a reverse osmosis water processor to remove pollutants and microorganisms. In European countries, though, such processing of natural mineral water (as defined by a European directive) is not allowed under European law. In practice, a fraction of the living bacteria can and do pass through reverse osmosis membranes through minor imperfections, or bypass the membrane entirely through tiny leaks in surrounding seals. Thus, complete reverse osmosis systems may include additional water treatment stages that use ultraviolet light or ozone to prevent microbiological contamination.
Radium Removal: Some groundwater sources contain radium, a radioactive chemical element. Typical sources include many groundwater sources north of the Illinois River in Illinois, United States of America. Radium can be removed by ion exchange, or by water conditioning. The back flush or sludge that is produced is, however, a low-level radioactive waste.
Different RO water filter systems handle a different number of purified gallons in a day. Normally this capacity goes from 50 to 150 Gallons per day and so on. You must identify the amount of water your family needs in a day. For Small families, reverse osmosis with 50 Gallons per day capacity is suggested while for larger families, Whole house Ro system with minimum 75-100 GPD is suggested.
There are multiple built in filters water bottles choices. Vestergaard's Lifestraw Go and Sawyers Personal Water Bottle are two examples. The Lifestraw Go filters specs say it will filter up to 1,000 liters (264 gallons) of water down to particulate matter larger than 0.2 microns Source Sawyer's Personal Water bottle absolute hollow fiber membrane inline filter down to 0.1 micron. Source
In 1904, Allen Hazen showed that the efficiency of a sedimentation process was a function of the particle settling velocity, the flow through the tank and the surface area of tank. Sedimentation tanks are typically designed within a range of overflow rates of 0.5 to 1.0 gallons per minute per square foot (or 1.25 to 2.5 litres per square meter per hour). In general, sedimentation basin efficiency is not a function of detention time or depth of the basin. Although, basin depth must be sufficient so that water currents do not disturb the sludge and settled particle interactions are promoted. As particle concentrations in the settled water increase near the sludge surface on the bottom of the tank, settling velocities can increase due to collisions and agglomeration of particles. Typical detention times for sedimentation vary from 1.5 to 4 hours and basin depths vary from 10 to 15 feet (3 to 4.5 meters).:9.39–9.40:790–1:140–2, 171